Q1: What type of signal does the boiler accept from BMS?
The standard controls can accept a standard DC signal, either 0(4)-20mA, or 2-10V, or 0-10V signals.
Q2: Are Gasmaster boilers controllable via internet connection?
This depends on the customer application but in many cases, the answer is yes.
Q3: What type of temperature controller is used in the boilers?
Gasmaster Industries uses both Omron and Siemens temperature controllers. For specific details on different models, contact your local Gasmaster Industries representative.
Q4: Is the blower speed constant or variable?
Most Gasmaster boilers have variable speed blowers. A constant speed option is available, contact a Gasmaster Industries sales representative for information regarding this option for different units.
Q5: Can we use sealed combustion with Gasmaster units?
Yes, sealed combustion may be used with Gasmaster units. Please contact a Gasmaster Industries sales representative to discuss particulars.
Q6: Are Gasmaster boilers on/off or modulating?
Gasmaster boilers are all fully modulating. On/off and 2-stage options are available if required.
Q7: Are spare parts readily available?
Yes. All parts and components used in Gasmaster boilers are off-the-shelf and readily available from major suppliers.
Q8: Can your boilers work in a lead-lag system?
Yes. All Gasmaster boilers can work efficiently in a lead-lag system. Contact a Gasmaster Industries sales representative for more details regarding this type of set-up.